by Ketut Dartawan, Amin M. Najafabadi
Pterra is presenting a paper on the above subject at the IEEE General Meeting 2017- Chicago 16~20 July. Abstract of the paper follows:
IEEE updated its recommended practice and requirement for harmonic control in electric power system after more than two decades. The most updated version of the standard (IEEE Std. 519-2014) revised the 1992 version and its static harmonic voltage and current limits. Unlike the 1992 and the older versions of the standard, the 2014 version introduces a newer approach which considers the stochastic nature of harmonic distortions. Furthermore, it recommends limits based on the number of times distortions may occur. For example, for the harmonic current distortion, it recommends three limits: daily 99th percentile, weekly 99th percentile, and weekly 95th percentile values. Applying the IEEE Std. 519-2014 for planning studies and for harmonic assessment of proposed projects can be very challenging because presently there is no known commercial tool which fully considers the stochastic simulations and limits required in the standard. This paper demonstrates the approach used by the authors in applying IEEE Std. 519-2014 to a harmonic study recently performed for a 180 MW solar farm.
Index Terms- harmonic analysis, harmonic filters, solar power generation, statistical analysis, time series analysis